Skip Maine state header navigation
Skip First Level Navigation | Skip All Navigation
|Home | Contact Us | Calendar||
Site Map |
OTHER PFR AGENCIES
New Board Action
October 17, 2008 - For existing dwellings, AFCI protection is not required when replacing electrical panelboards; however, AFCI protection is required for new branch circuits in accordance with 210.12(B) of the 2008 NEC.
October 17, 2008 - The Board approved illustration #30 in the CMP Handbook of Requirements for Electric Service and Meter Installations, effective August 25, 2006, which does not require a transition fitting between the PVC and steel so long as the bell end of the PVC is installed over a threaded end of the metal conduit.
If you cannot find the answer to your question, click HERE to send an e-mail message to the Electricians' Examining Board.
Last Updated: February 5, 2013
About This Board
|Copyright © 2006 All rights reserved.|